100X remote control floating ball valve is to rotate the valve love to make the valve open or closed. Ball valve switch light, small size, can be made into a large caliber, reliable sealing, simple structure, easy maintenance, sealing surface and spherical surface is often in a closed state, not easy to be eroded by the media, in various industries are widely used.
100X remote control float valve can effectively control the liquid level of water tower or water tank, cut off or open the spool input water flow or stop the water flow from leaking out when suitable, the liquid level control is accurate, the water level is not disturbed by pressure fluctuations, open and close tightly without leakage, the float is flexible and maintenance is simple. Suitable for the automatic water supply system of water tank, pool and water tower in high-rise buildings
Remote control float valve structure is relatively simple, relatively easy to maintain, the sealing surface and spherical surface is often in a closed state, not easy to be eroded by the medium, easy to operate and repair.
Mainly used for water tanks, water-specific. Commercial electric water boiler, heat pumps, air conditioning cooling towers, water storage towers, water storage tanks, etc., but at the time of installation to pay attention to several matters as follows.
1, remove the protective cover on both sides of the flange end of the remote control float valve, flush clean in the state of the valve fully open.
2, the pipeline near the installation point must not have low hanging or bear external force, you can use pipe support or support to eliminate the deviation of the pipeline.
3、Before installing the remote control float ball valve, the whole machine should be tested according to the specified signal (electric or pneumatic) (to prevent the vibration from affecting the performance due to transportation), and only after passing the test can be installed on line (wiring according to the electric actuator line diagram).
4、The remote float valve should be installed in the horizontal or vertical direction of the pipeline.
5、Before preparing to connect with the pipeline, flush and clear the residual impurities in the pipeline (these substances may damage the valve seat and ball).
6、After connecting with the pipeline, please cross-lock the flange connecting bolts with the specified torque.
7、During the installation of remote float ball valve, please do not use the actuator part of the valve as the lifting point for lifting to avoid damaging the actuator and accessories.
618 FLEX is a Chinese Supplier, specialized in Inox Valves and Inox Fittings.
Stainless Steel valves are inevitable in the production of GAS, OIL& WATER.
This product is made of stainless steel and durable to resist corrosion.
618 Flex Co.,Ltd. INOX VALVES COVERS ALL WATER, OIL, GAS PIPELINE SYSTEMS.